Passive Rogowski coils output a very low AC voltage, often somewhere between 20 – 150mV per 1000A.
Although measuring high amperage with no saturation, the coil inductance displaces the phase +90 degrees with respect to the input current.
Most meter manufacturers require 333 mV, 5A, 1A or some other (higher) signal output than what the Rogowski coils produce passively.
For this reason there is an “integrator” option.
The integrator does two things:
Amplifies the signal (typically to 333 mV or 5A or another commonly accepted signal)
Compensates for the 90 degree phase shift.
The eGauge has an ‘inbuilt’ integrator allowing Rogowski Coils to be directly attached.
For monitors requiring a 5A input
For monitors requiring a 333mVac input